The word points is used to describe data storage locations within a DDC system. Data can come from sensors or from software calculations and logic. Data can also be sent to controlled devices or software calculations and logic. Each data storage location has a unique means of identification or addressing.
Direct digital controls (DDC) data can be classified three different ways - by data type, data flow and data source.
Data type is classified as digital, analog or accumulating. Digital data may also be called discrete data or binary data. The value of the data is either 0 or 1 and usually represents the state or status of a set of contacts. Analog data are numeric, decimal numbers and typically have varying electrical inputs that are a function of temperature, relative humidity, pressure or some other common HVAC sensed variable. Accumulating data are also numeric, decimal numbers, where the resulting sum is stored. This type of data is sometimes called pulse input.
Data flow refers to whether the data are going into or out of the DDC component/logic. Input points describe data used as input information and output points describe data that are output information.
Points can be classified as external points if the data are received from an external device or sent to an external device. External points are sometimes referred to as hardware points. External points may be digital, analog or accumulating and they may be input or output points. Internal points represent data that are created by the logic of the control software. These points may be digital, analog or accumulating. Other terms used to describe these points are virtual points, numeric points, data points and software points.
Global or in-direct points are terms used to describe data that are transmitted on the network for use by other controllers. These points may also be digital, analog or accumulating.
Analog input points typically imply an external point and represent a value that varies over time. Typical analog inputs for HVAC applications are temperature, pressure, relative humidity, carbon dioxide and airflow measurements. Typical analog outputs include control signals for modulating valve positions, damper positions and variable frequency drive speed.
Typical digital inputs for HVAC applications represent the status (example: whether or not the motor is running) of fans, pumps, motors, lighting contactors, etc. A temperature high limit is considered a digital input because, although it is monitoring an analog value (temperature), the information that is transmitted to the controller is a digital condition (whether or not the temperature has exceeded a defined value). Digital outputs are typically motors or other devices that are commanded on or off. Digital outputs include fans, pumps, two-position (solenoid) valves, lighting contactors, etc.
A true analog output (voltage or current) is a varying DC voltage or milliamp signal that is used to drive a transducer or controlled device. Another type of analog output is pulse width modulation (PWM). PWM is accomplished by monitoring a timed closure of a set of contacts. The amount of time the contacts are closed is proportional to a level of performance for the controlled device.
There are basically three common approaches used to program the logic of DDC systems. They are line programming, template or menu-based programming and graphical or block programming.
Line programming-based systems use Basic or FORTRAN-like languages with HVAC subroutines. A familiarity with computer programming is helpful in understanding and writing logic for HVAC applications.
Menu-driven, database or template/tabular programming involves the use of templates for common HVAC logical functions. These templates contain the detailed parameters necessary for the functioning of each logical program block. Data flow (how one block is connected to another or where its data comes from) is programmed in each template.
Graphical or block programming is an extension of tabular programming in that graphical representations of the individual function blocks are depicted using graphical symbols connected by data flow lines. The process is depicted with symbols as on electrical schematics and pneumatic control diagrams. Graphical diagrams are created and the detailed data are entered in background menus or screens.
System architecture is the term used to describe the overall local area network or LAN structure, where the operator interfaces connect to the system and how one may remotely communicate to the system. It is the map or layout of the system.
The network or LAN is the medium that connects multiple intelligent devices. It allows these devices to communicate, share information, display and print information, as well as store data. The most basic task of the system architecture is to connect the DDC controllers so that information can be shared between them.
A control loop requires a sensor to measure the process variable, control logic to process data, as well as calculate an instruction, and a controlled device to execute the instruction. A controller is defined as a device that has inputs (sensors), outputs (controllable devices) and the ability to execute control logic (software) (Figure 7).
Communications between devices on a network can be characterized as peer-to-peer or polling. On a peer-to-peer LAN, each device can share information with any other device on the LAN without going through a communications manager (Figure 8).
The controllers on the peer-to-peer LAN may be primary controllers, secondary controllers or they may be a mix of both types of controllers. The type of controllers that use the peer-to-peer LAN vary between manufacturers. These controller types are defined later in this section.
In a polling controller LAN, the individual controllers can not pass information directly to each other. Instead, data flows from one controller to the interface and then from the interface to the other controller (Figure 9).
The interface device manages communication between the polling LAN controllers and the higher levels in the system architecture. It may also supplement the capability of polling LAN controllers by providing the following functions: clock functions; buffer for trend data, alarms, messages; and higher order software support.
Many systems combine the communications of a peer-to-peer network with a polling network. In Figure 10, the interface communicates in a peer-to-peer fashion with the devices on the peer-to-peer LAN. The polling LAN-based devices can receive data from the peer-to-peer devices, but the data must flow through the interface.
Controllers can be categorized by their capabilities and their methods of communicating (controller-to-controller). In general, there are two classifications of controller - primary control units and secondary control units
Primary controllers typically have the following features:
Secondary controllers typically have the following features:
The next critical element in the system architecture is an operator interface. Operator interfaces are required to:
There are five basic types of operator interfaces. They include:
Desktop computers are centralized operator workstations where the main function is programming, building and visualizing system graphics; long term data collection; and alarm and message filtering.
Notebook computers may connect to the LAN through a communication interface that stands alone or is built into another device. The notebook computer connected to the LAN at a particular level may not have the same capability as a computer connected to the LAN at a higher level.
Keypad liquid crystal displays typically are limited to point monitoring and control. They may have some limited programming capability, such as changing a set point or time schedule.
Handheld consoles, palmtops and service tools are proprietary devices that connect to primary controllers or secondary controllers. Typically they allow point monitoring and control, controller configurations (addressing and communication set-up), and calibration of inputs and outputs.
Smart thermostats are sensors with additional capabilities. They connect to secondary controllers and have a service mode to allow for point monitoring, control and calibration. They also have a user mode that allows point information to be displayed, setpoint adjustment and an override mode.
The communications interface shown in the Figure 11 is a communication interface device. It provides the path between devices that do not use the same communications protocol. This includes computers, modems and printers.
It may be a stand-alone component or it may be built into another device as shown in Figure 12.
Each communications interface on Figure 12 may:
When systems become larger than the capacity of a single sub-network, a higher level of architecture is added to allow the use of multiple sub-networks.
The site LAN wide area network or WAN is used to connect multiple sub-networks and site computers. Multiple sub-networks can be connected to a single site LAN/WAN that allows information sharing between devices on different sub-networks (Figure 13). There may be a limitation on the number of site computers. The site LAN/WAN may include routers if TCP/IP is used. If no routers are used, the protocol can be totally proprietary. If TCP/IP is used, the EMS site LAN/WAN can be the information system backbone within the facility or between facilities.
Multiple site computers can be added to the site LAN/WAN. They can connect the site LAN/WAN via a communications interface, which may be a router. Site LAN/WAN computers can send and receive information from the entire system. Information can be received by each of the site computers, but can not be subsequently shared from one computer to another. Sub-network computers may only be able to see their own sub-network.
Site LANs allow multiple computers to communicate with each other. They may use commercially available computer network software and hardware. Messages, alarms and other data can be re-routed to other computers on the primary site LAN. Information stored in other computers can be remotely accessed. This includes graphics, programming and stored trend and operational data.
Some vendors combine multiple functions into a single device. In the following system architecture, Figure 14, the communication interface is built into the primary controller. A peer-to-peer LAN or sub-network is connected directly to the device.
In Figure 15, the key component in the system consists of a communication interface, a primary controller and an interface to the secondary polling network.
The addition of a site LAN allows a system to gain size in terms of the number of devices that are served, but in some applications, the location of the devices, rather than the number of devices, is the bigger challenge. In this situation, modem-based communication is used to expand the geography of the system.
In auto-answer/auto dial systems, a specialized communication interface is substituted which introduces a modem and phone lines into the standard architecture. These communication interfaces are made with built-in modems or use external commercial modems. Auto-answer/auto-dial configurations are used to provide monitoring and access to remote buildings. They are used where traditional direct-wiring methods are impractical; and where central site monitoring is desired; or where remote access to controllers is desired.
In an auto-answer/auto-dial system, the central communications interface may call the individual sites or vice versa. Information and data can be passed to and from the layer above the central communications interface (Figure 16).
The auto-answer/auto-dial LAN architecture is typically used by installations with multiple facilities where control and monitoring needs to be centralized. Multiple LANs are used to maintain the groupings of devices, or to separate controllers into defined groups.
In a systems architecture, the local sites have the ability to call an alternate communication interface, if the primary is not available (Figure 17).
One-way dial systems, Figure 18, are typically used to enable system owners to access their systems from a remote location, such as their home. It is used where auto-dial monitoring is not required. It can also be used by the installation and service company or by the commissioning authority to troubleshoot and program from remote locations. One-way dial can also be used to dial into remote site LANs or sub-networks.
Two modems are required, one located at the remote computer and one at the system site. Typically, the DDC operating software must be installed on the remote computer.
Communication between two different devices controlling equipment, requires a common protocol, a common communication speed and known data formatting. Vendors build their devices around these criteria, so communication between devices by the same manufacturer is routine.
In many installations, it is desirable for a proprietary building DDC system to communicate with other proprietary DDC systems controlling pieces of equipment. Examples would include a building DDC system and a chiller DDC system (Figure 19) or a fume hood DDC system. Communication between the two systems will require an interface or gateway, due to different proprietary protocols, communication speeds and data formatting.
The gateway or interface translates protocol between the two proprietary systems. The proper operation of the gateway is dependent on the continued use of the specific revised levels of software on both systems. It typically requires the support of the manufacturer at the corporate level to implement and cooperation between the manufacturers. In addition, the costs can vary widely.
In the DDC world, there are the three classifications of protocols: closed protocol, open protocol and standard protocol.
A closed protocol is a proprietary protocol used by a specific equipment manufacturer. An open protocol system uses a protocol available to anyone, but not published by a standards organization. A standard protocol system uses a protocol available to anyone. It is created by a standards organization.
An open system is defined as a system that allows components from different manufacturers to co-exist on the same network. These components would not need a gateway to communicate with one another and would not require a manufacturer specific workstation to visualize data. This would allow more than one vendors product to meet a specific application requirement.
The sole use of an open or standard protocol does not guarantee that a DDC system will be an open system. A manufacturer has the ability to use open or standard protocols, yet create a closed system, thus continuing a building owners dependence on a single manufacturer. This can be accomplished by using unique communication speeds, unique data formatting and by not adopting the full range of an open protocol.
Note: A building owner/engineer should thoroughly research a manufacturers claim of an open system.
BACNET is a standard protocol published by a standards organization (American Society of Heating, Refrigerating and Air-conditioning Engineers or ASHRAE). It is a specification for a protocol. DDC vendors create a communication protocol that complies with this specification.
BACNET is a relatively complex standard. The standard defines protocol implementation conformance statements (PICS) that define different levels of compliance. A given vendor may or may not support the level required for a given application. In other words, a vendor could meet a very low level of compliance and be BACNET-compatible. The key question is, At what level?
In Figure 20 the chiller control units DDC will communicate with the building DDC system if each has a BACNET gateway and their PICS match.
If a vendor states their product is native BACNET, they are using the BACNET protocol in lieu of a proprietary protocol on their LAN. In Figure 20, a native BACNET building system would be able to communicate to the chiller control DDC with one less gateway.
An overlay system is a high-end workstation that communicates with multiple manufacturers proprietary EMS systems. An overlay system supplier creates drivers to talk to the different systems. The vendors must have a cooperative relationship and revision control is important for continued successful use. The workstation typically displays data, allows manual control and setpoint changes, and handles alarms and messaging. Any detailed editing of the control sequence will still require knowledge of the underlying proprietary software.
The Echelon Corporation has created an open protocol that uses a standard processor and a set of standard transceivers, which allows components from different manufacturers to co-exist on the same LAN. The protocol is available to anyone and is called LONTALK. A unique chip is required for any device that uses LON. Standard network variable formats have been established to allow the transfer of data from one device to another regardless of origin.
Presently, various vendors are competing to become the defacto standard for the network database structure. The network database is a map of the components and the relationship of the data moving between them. The operator workstation needs this structure to visualize the data.
Software suppliers providing the software for the operator workstation may be independent of those providing the software for the database structure and the EMS vendors.